You can download a limited, functional demo of EnergyPro from here. I will try to look at it when reaching HAP. Below is a screen shot showing a floor plan created from within Chvac. Learn more about ebook formats and e-readers.
|Country:||Republic of Macedonia|
|Published (Last):||13 March 2004|
|PDF File Size:||17.58 Mb|
|ePub File Size:||12.37 Mb|
|Price:||Free* [*Free Regsitration Required]|
Yoshicage Other outstanding features include ASHRAE Standard 62 analysis, automatic building rotation, degree wall orientations, tilted glass, exterior shading, internal operating load chvqc, variable indoor design temperatures, people diversity, pretreated outside air, seasonal infiltration and ventilation rates, reheat loads, duct gains and losses, and return air plenums.
Overview Chvac quickly and accurately calculates the maximum heating and cooling loads for commercial buildings. Should you have questions, you can email us at sales elitesoft. Software can be delivered to you via email in addition to the hardcopy being shipped to you. Am I missing something here? Export to EnergyPro Large Screen. All you have to do is enter square footage of the water surface, enter the water temperature, select an activity factor, and select an airflow velocity.
So if nothing is to be added on fan column, it simply puts zero, as calculation algorithm likely does not have subtraction at that column. Payment Methods With rare exceptions for government and educational entities, all orders must be prepaid with a check or credit card. Keep in cvac that a room is a single space, and that rooms can be grouped into air handling systems which in turn make up the building.
As a matter of reference, you can estimate the cost of shipping from some of these companies chhvac visiting their web site and entering the appropriate information for shipping from College Station, Texas to your location. Export to eQUEST when you want to analyze large commercial projects that require precise modeling of variable loads, equipment, operating schedules, and control schemes.
The maximum number of air handling systems allowed for any version is the number of rooms allowed orwhichever is the lesser. See the web links below. The program allows an unlimited number of rooms which can be grouped into as many as air handling systems. Sofware likely does not reduce loads but only adds it.
Elite Software Chvac 8. Click the button beside the Description column and a new Typical Lighting Loads dialog opens, which lets you choose from several lists of lighting items that come from tables in the and ASHRAE Handbook of Fundamentals.
Ductsize — Design and analyze complete duct systems. Multiple items of equipment cooling loads for each room. My second question is: All the important data is now on two tabs instead of three. However, downloaded demos do not include user manuals. The air handler data includes the fan and terminal type, the desired heating and cooling supply air temperatures and data for duct heat gains and losses.
Perform common electrical calculation and data look-up tasks. I never subtract internal heat gains from heat loss calculation. Chvac quickly and accurately calculates the maximum heating and cooling loads for commercial buildings.
Sloped Ceiling Area Calculator dialog. Here are just a few of its capabilities. Chvac free version download for PC Once connected, simply tell the Elite representative what programs you would like hcvac order. Performs comprehensive energy analysis and does evaluations of multiple compliance standards.
The program performs extensive checks on the data you enter and alerts you to any problems that it finds, such as a wall having too much window area, or a leaving coil temperature for an air handler outside of the expected range. Thank you for helping keep Eng-Tips Forums free from inappropriate posts. This dialog is filled with sensible and latent load information for various kinds of equipment listed in various tables in both the and ASHRAE Handbook of Eliite. Keep in mind that a room is a single space, and that rooms can be grouped into air handling systems which in turn make up the building.
Fixed a small problem on the Project Explorer window, where the vertical splitter bar in the middle would not remember its position if it had previously been positioned very far to the right. Fixed a problem with some of the inputs on some multi-row inputs, such as the roofs, walls and glass on the Zone Data window, where if you opened a project that had been previously edited on a system using a different decimal place than that of your current system, then some values could be changed from what they had been before. Fixed a problem in a few places in some of the reports when using a language other than English, where instead of the text saying "Yes" or "No" it would use the words of the current language. Fixed a bug that could happen on the built-in duct sizing for zone runouts and air handler main trunks, where if you had the "Use Schedule" input set to "Yes" it would not always use diameters or widths from the schedule.
ELITE CHVAC MANUAL PDF
This computer program calculates the maximum heating and cooling loads in commercial and industrial buildings. This calculation technique allows the programs to calculate for any building orientation and still produce output results that can be easily verified by hand. Program Input CHVAC is a true Windows program that uses all the latest data entry techniques such as toolbars, hyper linked help, and form tabs. All input data is checked at the time of entry so that no improper data can be entered. Five types of data are requested: general project data, outdoor design data, building material data, air handler data, and specific zone data. The general project data includes the project and client name, designer, building opening and closing hours, internal operating load schedules, and any desired safety factors. The outdoor design data includes the summer and winter outdoor design conditions automatically looked up for you if a city reference is given and the desired ventilation and infiltration rates.
Elite Software Chvac 7.01.169
Easier and Better Glass Definitions: The Drawing Board window enables you to enter your room data by simply drawing the floor plan on the screen. Traditionally, this data has simply been transferred using a manual entry process. The program performs extensive checks on the data you enter and alerts you to any problems that it finds, such as a wall having too much window area, or a leaving coil temperature for an air handler outside of the expected range. If you are familiar with the data that CAD programs typically write to gbXML files, you know that material definitions are usually incomplete for purposes of load calculation, since they do not usually include data such as wall U-values or roof ASHRAE numbers. Manual D Ductsize Online.